Midfield, AL HVAC Service and Repairs
Perfect Service provides air conditioning, heating, and home performance services to the residents of Adamsville, AL and the surrounding areas. Call us today at 205-957-2022 for more information about our services or to get an estimate.
Read our reviews and find out why your neighbors consider us to be the experts for HVAC repair, replacement, and maintenance in Adamsville, AL.
for Midfield, AL
Our Reviews by City
great service tech
MARCUS - Midfield, AL
The technician was very prompt, professional courteous and knowledgeable
SHAJUANNA - Midfield, AL
The technician was proactive in discovering & treating potential problems and also helpful in solving current problems. I have been with perfect service for over 10 years and have always received great service. thank you
Team Perfect Service .
CLEAN AND CHECK HT. CHECK THERMOSTAT, CHECK AIR FILTER, CHECK BURNERS AND BURNER OPERATION, CHECK HUMIDIFIER, CHECK ALL ELECTRICAL CONNECTIONS, CHECK HEAT EXCHANGER, CHECK HIGH LIMIT CONTROL. LUBRICATE ALL NECESSARY MOVING PARTS, ADJUST BLOWER COMPONENTS. EVERYTHING IS RUNNING GREAT.
SOLD WTY BUYBACK 3TON GASPAC REDO RETURNS W/ADC. MADE SURE SYSTEM WAS INSTALLED PROPERLY. MADE SURE WORK AREA WAS CLEAN WHEN FINISH. CHECK THERMOSTAT, CHECK ALL ELECTRICAL CONNECTIONS, CHECK AIR FILTER, CHECK GAS PRESSURE AND FOR PROPER VENTING. EVERYTHING IS RUNNING GREAT.
Team Perfect Service .
CLEAN AND CHECK A/C. CHECK THERMOSTAT, CHECK AIR FILTER, CHECK CONDENSER COIL, CHECK FREON LEVELS. FOUND BAD CAPACITOR, HAD TO REPLACE. CHECK DRAINAGE, CHECK ALL ELECTRICAL CONNECTIONS. ADJUST BLOWER COMPONENTS, LUBRICATE ALL NECESSARY MOVING PARTS. EVERYTHING RUNNING GREAT.
CLEAN AND CHECK A/C. CHECK THERMOSTAT, CONDENSER COIL, CHECK AIR FILTER, CHECK AIR FLOW, CHECK ALL ELECTRICAL CONNECTIONS, CHECK DRAINAGE, CHECK FOR PROPER ENERGY CONSUMPTION. ADJUST BLOWER COMPONENTS, LUBRICATE ALL NECESSARY MOVING PARTS. EVERYTHING IS RUNNING GREAT.
Birmingham Alabama Hvac service on a 6 year old Temp-Star and a 6 year old Heil unit. Check and clean coil condenser, adjust blower components making proper adjustments and cleanliness of blower and components are nessassary for adequate air flow.
Air Conditioning service. Diagnose, clean and performed annual AC maintenance and tune-up for service plan on Heil Cooling System. Cleaned condenser coil on outdoor air conditioner unit, check Freon pressures, cleared drain lines, oiled necessary moving parts, on 4 year old central HVAC system with R-410a. Heating and cooling maintenance complete which will help lower cooling cost for this residential customer. Cooling system is now ready for summer weather.
Technician came out on an annual service cleaning for the summer. Cleaned the outdoor unit, checked all the wiring, oiled moving parts, cleaned outdoor coil, also cleaned indoor evaporation coil. Checked all the inside equipment, duct work, thermostat. The customer is now ready for the summer months ahead.
CLEANED, TUNED UP, AND SAFETY CHECKED 6 YEAR OLD AC SYSTEM, INSTALLED UV, AND ALSO INSTALLED UV LIGHT.
cleaned ac system, also cleaned air ducts and installed uv light. enlarged return vent, included service agreement.